Pragma surface enclosure - IP30 - 6 x 24 modules - without doorShow more characteristics >
Main rangePragma product or component typeEnclosure enclosure typeDistribution enclosure width550 mm height1050 mm depth148 mm number of 18 mm modules per row24 number of horizontal rows6 electrical insulation classClass IIDouble insulation provided equipmentMarking kit ( 1 )Terminal block ( 2 )Identification label ( 1 )Blanking plate strip ( 1 ) Complementary enclosure mountingSurface 9 mm pitches48 total number of 18 mm modules144 power dissipation in W100 W [In] rated current160 A type of railMultifix cable entryCut-out platesCable or tubeTrunkingRemovable plates number of terminal blocks1 earth terminal block with 32 Quick outgoers1 neutral terminal block with 35 Quick outgoers distribution block outgoers1 x 50 mm² for earth1 x 50 mm² for neutral28 x 6 mm² for earth28 x 6 mm² for neutral3 x 25 mm² for earth6 x 25 mm² for neutral enclosure materialBack part : technoplasticFront face : technoplasticBack part : metalFront face : metal colourEnclosure : white ( RAL 9016 )Front face : grey ( RAL 7004 ) market segmentSmall commercialResidential targeted countryGreeceFinlandRussiaSwedenBalticHungaryCzech republic Environment fire resistanceBack part : 650 °C conforming to IEC 60695-2-1Front face : 650 °C conforming to IEC 60695-2-1 IP degree of protectionIP30 without door conforming to EN/IEC 60529IP40 with door conforming to EN/IEC 60529 IK degree of protectionIK08 without door conforming to EN/IEC 62262IK09 with door conforming to EN/IEC 62262 overvoltage categoryII ambient air temperature for operation-25...60 °C standardsIEC 62262IEC 60947-7-1EN 60695-2-11IEC 60529IEC 60695-2-11EN 60439-3IEC 60439-3 Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
CADSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.