insulation monitoring XML308 Vigilohm - 115..127 V AC 50/60 Hz - failsafeShow more characteristics >
Main range of productVigilohm device short nameXML308 type of measurementNetwork insulation resistance, earth leakage capacitance, local measurement signal contacts composition3 C/O earthing systemIT display typeLCD scale0.1...999 kOhm number of channels8 measurement current0...5 mA measurement voltage6 V fail safe featureWith [Us] rated supply voltage115...127 V AC, 50/60 Hz (tolerance: - 15...10 %) mounting positionHorizontal mounting Complementary [Ue] rated operational voltage<= 1000 V AC, 45...400 Hz (device connected to phase with PHT1000 subassembly)<= 1200 V DC (device connected with PHT1000)<= 1700 V AC, 45...400 Hz (device connected to neutral with PHT1000 subassembly)<= 440 V AC, 45...400 Hz (device connected to phase)<= 500 V DC<= 760 V AC, 45...400 Hz (device connected to neutral) signalling functionAlarmDevice faultInsulation value displayTransient fault polling time15 s test functionManual, self test breaking capacity10 A at 24 V DC, L/R = 1 ms0.45 A at 220 V DC, L/R = 1 ms0.65 A at 120 V DC, L/R = 1 ms2.5 A at 48 V DC, L/R = 1 ms5 A at 230 V AC, cos phi = 0.73 A at 400 V AC, cos phi = 0.7 power consumption in VA<= 30 VA mounting modeFlush-mounted mounting supportCubicleEnclosurePlate height129 mm width229 mm depth213.5 mm product weight4.5 kg tamperproof of settingsProtected by access codeProtected by sealable cover auxiliary connection terminalTunnel type terminals, cable cross section: 0.75...1.5 mm² flexibleTunnel type terminals, cable cross section: 1...1.5 mm² rigid Environment dielectric strength2500 V IP degree of protectionIP30 standardsIEC 364 ch 4 and 5IEC 61557-8NF C 15-100 §413.4UTE C 63-080 classes CPI/XA, DLD/M ambient air temperature for operation-5...55 °C ambient air temperature for storage-20...70 °C Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.