|FA12170||What is the maximum motor cable length allowed for Altivar 11 Drive.|
The maximum motor cable length allowed for Altivar 11 Drive is as follows:
50 meters -- Shielded cable
100 meters -- Non-Shielded cable
|FA12203||Can the Multi 9 range MCB be reverse fed.|
Yes, the Multi9 miniature circuit breakers (MCBs) can be fed either from top or bottom without any deterioration of their characteristics.
|FA232984||APC Switched Rack PDUs - any pending outlet commands are lost when PDU Network Management Interface is rebooted |
If an APC Switched Rack PDU's Network Management Interface is rebooted (manually by the user, or automatically due to network watchdog timer...
|FA231199||Are there Windows or Linux drivers for the NBAC0226 USB to serial cable. |
There are no drivers available for the NBAC0226 serial to USB cable.
NetBotz Serial devices...
|FA226483||KVM1116P, KVM2116P, and KVM2132P KVM Switches using standalone WinClient and Java Client - Compatibility/Video Issue|
When using the WinClient or Java Client with my KVM1116P, KVM2116P or KVM2132P IP KVM Switch, why is my video distorted (as seen below)?
|FA21083||What is the insulation voltage rating for cables BMX FTW and BMX FCW in Modicon M340 range.|
The dielectric withstanding (VDC) for cables BMX FTW and BMX FCW is 1000 Volts applied for 1 minute and th minimum specific insulation resistance...
|FA12217||Can TeSys range overload relays be used in DC application.|
The overload relay with the bimetal technology (Thermal Overload) only can be used in DC application. Tesys LRD RangeTesys LRD thermal overload relays...
|FA12219||How to mount the Rectifier DR5TE on TeSys F range of contactor.|
The DR5TE4U rectifier is mounted separately off the coil on a little support sold with the coil. Refer attachment for the mounting instruction of...
|FA12215||Can TeSys T be used downstream of Altivar range Variable Speed Drive.|
The Current Transformers (CTs) of TeSys T are deigned to work under the frequency range between 47 to 63 Hz only. However, the output frequency range...
|FA12213||Is it possible to use TeSys GV2 and TeSys GV3 Range MPCB in DC applications. |
The TeSys GV2 and TeSys GV3 range MPCB can be used in DC applications as per their technical specifications.
Refer the below wiring connection for...