Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric Malaysia Website×
Actually Vijeo Citect reads digital addresses in blocks of 16 bits. So if there is a digital tag at C1000, Citect will read from C993 to C1008 in a single request. If the address C993 does not exist then 'address out of range' error comes. Because of this optimization of digital read requests make sure that there are valid addresses in the PLC. In some PLCs the valid ranges of all memory addresses can be set and make sure that the setup in the PLC is what Citect is going to read. If the range cannot be adjusted then do not use any digital tags within the first and last 16 digitals.
Vijeo Citect also tries to block reads together and may try to read across invalid addresses. So if C1000 and C1100 are configured, Citect will try to read from C993 to C1105. If any address is invalid between these tags then also 'address out of range' error comes. This is quite unlikely as almost all PLC contain continuous memory with no holes.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!