The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric Malaysia Website×
Yes, two smaller Line Chokes can be connected in series for Altivar 31/61/71 Drives.
The drop voltage of Line Choke is approximately 3% of the supply voltage at nominal current. For two series connected Line Chokes he drop voltage will be approximately 6%. So care must be taken to compensate this voltage drop, by supplying the Drive with a minimum of nominal Line Voltage plus 6% (Example for 400V supply, it should be 424V).
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!