Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric Malaysia Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
In the TN-C Network, it is prohibited to cut earth cable, as the Earth Cable is linked with the neutral of the System.
When ID-RCCB is connected on the TN-C Network, the protection conductor of the RCCB will not differentiate the PE conductor and Neutral conductor, as the PE Conductor and the Neutral are connected together in the TN-C Network. The RCCB will not be able to detect the potential variations that would arise due to operating current and insulation defect currents in this scenario and will fail to provide any protection. In fact it might cause nusciance tripping also.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!